Window Trickle / Slot Vent – 595mm
Each window trickle vent will give you the following equivalent area:
- 1no. window trickle vent 595mm long – 5000mm2 (2no. slots routed into window 245mm x 15mm)
- 2no. window trickle vent 300mm long – 2500mm2 each (1no. slots routed into window 245mm x 15mm each)
This trickle vent can be used on one large window, or split between 2 small windows to achieve the required equivalent area.
Independently tested to BS EN 13141-1:2004
Window Trickle / Slot Vent Description
Window trickle / slot vents are an excellent way of adding extra ventilation to your rooms. A trickle vent will help with condensation forming on your windows. You can control the level of ventilation you require using the finger tabs. Close one tab to reduce the amount of air flow, or close both tabs to stop the air flow
A lot of housing authorities now require landlords to meet the current ventilation requirements. This means drilling a large hole in the wall for a vent, or retro fitting the windows with trickle vents. The easier and cheaper option will fitting trickle vents.
Information on Building Regulations For Window Trickle Vents
The current Irish building regulations (Technical Guidance Document Part F – Ventilation) require that every *habitable room have a vent or vents giving a minimum equivalent area of 5000mm2.
“*Habitable room: A room in a dwelling used for living or sleeping purposes but does not include a kitchen having a floor area of less than 6.5 m2.”
Taken from Table 1 – Technical Guidance Document Part F – Ventilation 2009
Basic ventilation provision using background ventilators
Minimum equivalent area of background ventilator
- Habitable Room – 5000mm2
- Kitchen – 2500mm2
- Utility Room – 2500mm2
- Bathroom – 2500mm2
- Toilet (no bath or shower) – 2500mm2
The top of the sash is the ideal place to fit the trickle vent. As the sash can be removed from the window and worked upon on a bench or table. It is recommended to seal the outside section of the trickle vents with silicone sealant to seal against rain. We recommend Parasilico silicone sealant
Some window manufacturers use steel re-enforcing in their sashes as well as their frames. Regular routers and router bits are not designed to cut through steel. The only way of knowing for sure if there is re-enforcing in your sash is to drill two or three small holes. The top edge of the sash is the best place to do this as the holes won’t be seen. Carefully drill down through the top layer of uPVC. If there is re-enforcing present it will be directly under this top layer of uPVC.
The above information is intended as guide only. Please fully read (Technical Guidance Document Part F – Ventilation) to determine the ventilation requirements for your property.
This super versatile vent has a modular design. For making 1no. 595mm vent, take two matching sections of the vent (eg. two external sections or two internal sections) and simply click each side into the joiner. When fitted to the window click on the two end caps and joiner cap. For making a 300mm vent, simply fit as normal and click on the two end caps